A copy of this work was available on the public web and has been preserved in the Wayback Machine. The capture dates from 2012; you can also visit <a rel="external noopener" href="http://www.cse.psu.edu/~bhuvan/papers/ps/isca11.pdf">the original URL</a>. The file type is <code>application/pdf</code>.
<i title="Association for Computing Machinery (ACM)">
<a target="_blank" rel="noopener" href="https://fatcat.wiki/container/35q3ync5nbhnjfpylznlz57lyi" style="color: black;">SIGARCH Computer Architecture News</a>
Datacenter power consumption has a significant impact on both its recurring electricity bill (Op-ex) and one-time construction costs (Cap-ex). Existing work optimizing these costs has relied primarily on throttling devices or workload shaping, both with performance degrading implications. In this paper, we present a novel knob of energy buffer (eBuff) available in the form of UPS batteries in datacenters for this cost optimization. Intuitively, eBuff stores energy in UPS batteries during<span class="external-identifiers"> <a target="_blank" rel="external noopener noreferrer" href="https://doi.org/10.1145/2024723.2000105">doi:10.1145/2024723.2000105</a> <a target="_blank" rel="external noopener" href="https://fatcat.wiki/release/qxv3gcldtjfgjctgadfl4kez2e">fatcat:qxv3gcldtjfgjctgadfl4kez2e</a> </span>
more »... s" -periods of lower demand, which can be drained during "peaks" -periods of higher demand. UPS batteries are normally used as a fail-over mechanism to transition to captive power sources upon utility failure. Furthermore, frequent discharges can cause UPS batteries to fail prematurely. We conduct detailed analysis of battery operation to figure out feasible operating regions given such battery lifetime and datacenter availability concerns. Using insights learned from this analysis, we develop peak reduction algorithms that combine the UPS battery knob with existing throttling based techniques for minimizing datacenter power costs. Using an experimental platform, we offer insights about Op-ex savings offered by eBuff for a wide range of workload peaks/valleys, UPS provisioning, and application SLA constraints. We find that eBuff can be used to realize 15-45% peak power reduction, corresponding to 6-18% savings in Op-ex across this spectrum. eBuff can also play a role in reducing Cap-ex costs by allowing tighter overbooking of power infrastructure components and we quantify the extent of such Cap-ex savings. To our knowledge, this is the first paper to exploit stored energy -typically lying untapped in the datacenter -to address the peak power draw problem.
<a target="_blank" rel="noopener" href="https://web.archive.org/web/20120106121222/http://www.cse.psu.edu/~bhuvan/papers/ps/isca11.pdf" title="fulltext PDF download" data-goatcounter-click="serp-fulltext" data-goatcounter-title="serp-fulltext"> <button class="ui simple right pointing dropdown compact black labeled icon button serp-button"> <i class="icon ia-icon"></i> Web Archive [PDF] <div class="menu fulltext-thumbnail"> <img src="https://blobs.fatcat.wiki/thumbnail/pdf/b1/45/b145a2ee9ba5f842ffd94630f689e4d1b21bd533.180px.jpg" alt="fulltext thumbnail" loading="lazy"> </div> </button> </a> <a target="_blank" rel="external noopener noreferrer" href="https://doi.org/10.1145/2024723.2000105"> <button class="ui left aligned compact blue labeled icon button serp-button"> <i class="external alternate icon"></i> acm.org </button> </a>