A copy of this work was available on the public web and has been preserved in the Wayback Machine. The capture dates from 2022; you can also visit the original URL.
The file type is
The refurbishment of the Lipno I TG2 Francis turbine, situated on River Vltava, with maximum net head of 165 m and required operational range from 0 to 67MW of turbine power was performed in 2014. The new hydraulic design of the spiral case, distributor and runner was developed for this project. After about 1000 hours of operation the site inspection was performed and the cracks were found on 8 runner blades of 17 blades altogether. The all cracks were found near runner hub beginning from thedoi:10.1088/1755-1315/49/7/072011 fatcat:uejoynk7tjd3vnigzirflw5nge