A copy of this work was available on the public web and has been preserved in the Wayback Machine. The capture dates from 2018; you can also visit the original URL.
The file type is
Proceedings of the 2016 4th International Conference on Machinery, Materials and Information Technology Applications
In the process of supervision and inspection of Jiangxi power grid, there are some phenomena in 35kV Xin'an substation, such as abnormal sound from transformer and capacitor, and overheating in capacitor. The bus and capacitor power quality test found serious harmonic exceeding. Two methods of harmonic control are proposed, and the comparison of the control effect is carried out. Through the simulation of ETAP, the two methods are able to reduce the harmonic to the national standard and achievedoi:10.2991/icmmita-16.2016.68 fatcat:7iphbcpnbnagxcewikm37ycu3q